Experiences with a Large Scale He II Refrigeration system at Tore Supra
A cryogenic system (1,2) which has a capacity of 300 W at 1.75 K, 1000 W at 4 K and 30 kw at 80 K has been operating for more than 10 years. It is used to cool the superconducting toroidal magnet of the TORE SUPRA Tokamak (3). The 1.75 K refrigeration stage is constituted by 3 HeII saturated baths (cold sources) linked to the 18 HeII pressurized baths of the toroidal coils. The HeII saturated bath pumping system is achieved part at low temperature by two centrifugal compressors, part at room temperature by two oil ring pumps. This pumping system has a very large pumping range characteristic from 0.003 to 0.040 kg/s and a great operating reliability. The safety devices protections against quench are peculiar.
Bibliographic Reference: Article: Advances in Cryogenic Engineering 43(1998), 571-579
Record Number: 199910526 / Last updated on: 1999-03-26
Original language: en
Available languages: en