Periodic Reporting for period 2 - SafeAST (Continuous structural condition tank integrity monitoring of Above Ground Storage Tanks, aka “SafeAST, no entry: no empty.”)
Reporting period: 2016-12-01 to 2017-11-30
The monitoring technology, which has been under development at Plant Integrity for a number of years, involves the use of low frequency ultrasound to examine the whole of the tank floor from a number of permanently attached sensors around the perimeter on the outside. The long distance propagation characteristics of the ultrasonic waves used allow signals from one side of the tank to be picked up by a sensor on the other side (up to 30m diameter). By using combinations of transmit and receive amongst the set of sensors, it is possible to cover the whole floor area. By taking readings from the sensors regularly, long term trends in the condition of the floor can be determined. In this way, short term variations, for example from temperature fluctuations or changes in the fill levels in the tank, can be separated from changes in the physical condition of the floor. In this way, tanks needing priority attention may be identified and the more rigorous internal examinations may be concentrated on these.
The main goal of the project is to provide performance data to demonstrate the capability of a non-invasive ultrasonic guided wave monitoring system to detect time dependent degradation of the Atmospheric Storage Tank (AST) floors that may give rise to leaks.
Specific objectives are:
• Instrumentation and remote monitoring of specified tanks at identified refineries;
• Generation of condition reports on tank floors monitored;
• Review of detection and assessment performance of the non-invasive system in comparison with internal inspection (MFL, ultrasonic and visual) results;
• Production of a report detailing capabilities and limitations of the system
Tank floor monitoring system data may be gathered at pre-determined intervals while the tank is in operation so that monitoring without service interruption can be achieved. The test results are stored in the unit itself and external hard disks and also are copied on Pi servers at intervals for archiving and analysis.
* System requirements and system specification documents have been produced to guide the development.
* The sensor installation process has a significantly tighter focus on the surface preparation and bonding of the sensors to promote uniform coupling characteristics between the transducers and the chime and to have a robust system for reliable monitoring.
* Hardware and software developments were completed.
* Validation of equipment and system performance has been completed at experimental facilities and on operational tanks.
* There has been also important dissemination and explaoitation activities took place (including developing promotional material and exhibitions) during the second reporting period.
The use of non-invasive monitoring will allow:
• Internal inspection intervals to be extended for tanks with minimal degradation,
• Identification of tanks that require action for examination and repair before the assumed time for the next inspection is reached.
The long-term benefits of the application of non-invasive technology are:
• Significant savings in the direct costs of taking tanks out of service on a time-interval basis, as high priority tanks can be identified and taken out of service on the basis of need
• Savings in the indirect consequential costs of taking tanks out of service, in terms of the need for additional storage capacity;
• Improved knowledge based long-term planning of outages and minimisation of disruption to fluid management operations;
• Reduction in the likelihood of leaks occurring in tank floors and associated environmental contamination, through prioritisation of tank investigation and repair.
• Reduced risk of catastrophic failure, pollution, loss of inventory, fire and explosion.
• Reduced risk to human life sue to less interference with polluted environments